posted on 4/20/2009
I have a Carrier furnace model 58PB12510LA, I beleive the door switch is bad, it has a black wire, from the main, going to one terminal and a red wire & red/black wire both going to the other terminal. Can I wire around the switch to determine if that is the problem? If so would I just connect all the wires together?
All the comments are property of their posters.
Images, logos, content and data are © copyright by HVACWARE.COM. All Rights Reserved.
HVACWARE.COM is not responsible or liability for any content.
CLICK Here for the Old HVACWARE Forum