posted on 11/2/2007
My ducane furnace wouldn't light after working fine last winter. I found the orifice that the vacuum hose plugs into on the heat exchanger was plugged. I cleaned it out & it fired right up. I hope this might help.
replied on 11/7/2007
That is getting more common with these induced draft furnaces.
All the comments are property of their posters.
Images, logos, content and data are © copyright by HVACWARE.COM. All Rights Reserved.
HVACWARE.COM is not responsible or liability for any content.
CLICK Here for the Old HVACWARE Forum