posted on 12/11/2006
I have a Tempstar split system AC/Gas Furnace that was installed in 1996 that will not ignite. I got up in the attic and removed the front panel to check if the valve or the igniter was the problem. I could hear the valve open but the igniter would not light the pilot. After several seconds, the valve closed. After trying a couple of things, I wiggled the igniter plug where it plugs into the valve assembly. This caused the igniter to begin working. I cycled the furnace several times to insure that it would continue to work. When I got up this morning, I discovered that the furnace was no longer working. Do I need to replace the entire valve assembly, or is there a way to just replace the electronic control module connected to the valve? Or could this be some other problem?
All the comments are property of their posters.
Images, logos, content and data are © copyright by HVACWARE.COM. All Rights Reserved.
HVACWARE.COM is not responsible or liability for any content.
CLICK Here for the Old HVACWARE Forum